- 600 Pound Test
- Rubber Lined
- 1", 1-1/2", 1-3/4", 2", 2-1/2"
- UL Listed
|Lengths:||Standard lengths are 50, 75 and 100 feet.|
|Colors:||yellow, orange, red, tan, black, blue and green|
Quality: The fire hose assembly supplied under this specification shall be
constructed with superior quality materials.
NFPA 1961 standards shall be observed in production of the assembly, in order to
ensure its quality and durability.
Hose furnished under these specifications will have a potential service life
warranty of not less than five years; barring mistreatment that
would render it unfit for service.
Upon delivery, the hose shall be free from defects in workmanship and materials.
Any defective hose will be replaced at no charge.
The jackets will be woven evenly and be free of defects, including knots,
lumps, or unsightly disfigurations that could jeopardize the integrity of the
The warp yarn shall consist of staple polyester yarn.
The use of filament or entangled yarn is expressly forbidden due to the lack of
inherent abrasion resistance.
The filler yarns shall be constructed of high strength, low elongation, filament
polyester to reduce weight and increase flexibility.
Hose assemblies are available with polymer impregnation that provide additional abrasion resistance.
Colors include: yellow, orange, red, tan, black, blue and green.
Color shall be pure and even in each hose.
Impregnated hose shall meet the requirements of Mil-H-24606B for abrasion
The rubber lining shall be a single-ply extruded tube of synthetic EPDM
compounded to resist ozone.
The finished form shall be free of pits or other imperfections and have a smooth
No reclaimed rubber shall be used.
Plastic tubes that sacrifice durability of the hose life for the sake of weight
are not acceptable.
The backing shall be of adequate thickness to create a smooth waterway but
not greater than .020.
The fire hose constructed under this specification shall be manufactured fully
Tensile Strength & Ultimate Elongation:
Shall meet the standards of Underwriters Laboratories, Inc.TM as well as all
other properties of UL-19 for rubber lined hoses.
A valid U.S. Underwriters inspection procedure shall be in force at the time of bid.
||Twist per foot
||Request a Quote
Beginning at a point not less than four feet from the end, each fifty foot
section shall be stenciled in indelible ink with letters at least one inch high
stating the name of the manufacturer, month and year of manufacture, and service
test to 300 PSI. The ink used will be of a contrasting color.
Methods of Testing: All measurements and tests necessary to determine
compliance of the fire hose specified requirements shall be made with ASTM, UL
and NFPA 1961 designation, unless otherwise prescribed.
CouplingsAs required by purchaser, expansion ring threaded, STORZ clamp ring, etc.
per 50’ length
per 50’ length
are advised that special diameters or construction characteristics
produced on special request. For more information, please
contact your JGB Sales Representative.